possible passive cooling via a dry cooler
Design basis Central cooling solution
= 197 kW at water outlet (to laser source) of 19° C
79 kW in active cooling mode (compressor/pump/fan power)
25.7 kW in passive cooling mode = free cooler (pump/fan capacities)
Cooling capacities 300 kW to 1,000 kW.
- Air-cooled chillers for indoor/outdoor installation
- Cooling capacities between 300 kW and 1,000 kW
- Especially for applications with high cooling requirements
- Particularly high reliability with the lowest possible energy consumption.