Central cooling system via chiller and dry cooler with
additional targeted waste heat utilization via integrated heat pump
Passive cooling via a free cooler and waste heat utilisation via heat pump.
Design basis centralised cooling solution
= 197 kW at water outlet (to laser source) of 19° C
Cooling capacity heat pump 103 kW.
Heating capacity heat pump 140 kW at 65° C heating flow.
Central cooling system via chiller and free cooler with additional targeted waste heat utilization via integrated heat pump.
passive cooling via a free cooler and waste heat utilisation via heat pump.
79 kW in active cooling mode (compressor/pump/fan outputs)
25.7 kW in passive cooling mode = free cooler (pump/fan capacities)
37 kW electrical power heat pump with additional 103 kW cooling capacity and 140 kW heat output at 65° C heat source outlet (heating flow)
Heat pump system solution.
Cooling, Heating, using waste heat & preparing hot water.
- With a heat pump, the cooling and heating requirements can be efficiently combined in an overall concept.
- Waste heat from production processes can be used in a targeted manner.
- Previous energy costs for the generation of heat requirements are thus reduced.
- CO2 emissions, operating costs as well as maintenance and servicing costs are sustainably reduced.